If you experience any problems with eGauge or one of its accessories, please review the documentation available on this page. If these do not help resolve the problem, please contact tech support via email at:email@example.com
If your product has phone in support, feel free to contact us at
Provided you are connected to the device directly through your LAN (not through egauge.net) you can enter username "owner"' and password "default''. You can ensure that you're directly connected to the device by clicking the "LAN Access'' link at the top right of the device web pages.
|Register||Which register should appear in the defined style|
|Color||Color for the chosen register|
|Line||Line style and thickness|
|Sign||Whether to style the line for positive, negative, or both sign|
This answer applies only when a Netgear HomePlug 1.0 adapter is in use! With Actiontec adapters (or any Turbo-mode HomePlug adapter), there is no issue connecting to Cisco Catalyst switches. Also, this question only applies to professional-grade Catalyst Cisco products, not to Cisco home routers or switches.
Jan 6 19:41:46 192.168.1.15 1041767: 1041766: Jan 6 19:41:46.038 MST: %ETHCNTR-3-HALF_DUX_COLLISION_EXCEED_THRESHOLD: Collisions at FastEthernet0/14 exceed threshold. Considered as loop-back. Jan 6 19:41:46 192.168.1.15 1041768: 1041767: Jan 6 19:41:46.038 MST: %PM-4-ERR_DISABLE: loopback error detected on Fa0/14, putting Fa0/14 in err-disable stateTo work around this issue, change the switch configuration to force full-duplex mode on the port. That is, turn off auto-negotiation and force the port into full-duplex mode, even though the HomePlug adapter advertises itself as a half-duplex device only. Alternatively, replace the HomePlug adapter with a Turbo-mode adapter (85Mbps).
First, power-cycle the eGauge. See the answer to the next question "How do I power-cycle the eGauge?" for details on how to do this. Second, try unplugging the HomePlug adapter and then plugging it back in. This retrains the HomePlug-adapter and will often bring the device back.
Third, let's find out if the device can be accessed locally. We will use DEVNAME as a stand-in for the name of your device (e.g., for eGauge9999 or whatever the real name of your device is). Using a computer that is connected to the same LAN as the eGauge, open a browser and open one of the following two URLs, depending on the type of your computer:
If this URL loads and you get a graph that's updating, the eGauge is working fine and accessible through your LAN. If the URL does not load, check the following:
Fourth, let's find out whether the eGauge is connected to the server at egauge.net. Open a browser on a computer and try to load this URL:
If the page loads fine and results in a graph that's updating, your eGauge is fully operational. If the page does not load, it indicates a problem in your LAN environment. For example, the DCHP server on your LAN may be handing out incorrect Internet information. Please consult an IT professional for further help.
You may use the complete guide, Tutorial 6: Directly Connecting to the eGauge
Here are the recommended steps to establish communication with an eGauge when the HomePlug adapter or eGauge Ethernet port is directly connected into the Ethernet port of a computer:
1. Configure the computer's Ethernet-port to a static IP address of 192.168.1.11. The exact steps to do this vary with the operating system of the computer. For Mac OS X, this can be done by clicking on the Apple Menu's "System Preferences", then on "Network Control Panels". For Windows, this can be done by starting the "Control Panel", then selecting the "Network and Sharing Center". For Linux, this can be done by selecting "System", then "Administration", then "Network Tools".
2. Power-cycle the eGauge main unit (turn off the breakers it is wired to, wait for 5 seconds, then turn them back on).
3. If you can see the Status LED of the eGauge, it should be blinking green/cyan (light-blue) now.
4. Open a browser on the computer, then type the address
http://192.168.1.88into the browser's location bar, then press the Enter key.
5. At this point, you should be connected to the device.
|HomePlug AV PWR500|
|HomePlug AV PWR500||LED Label||Function||Typical Behavior||Other Behavior|
|PWR||Indicates the adapter has power||Green light||No LED - no Ethernet communication for too long or not receiving power|
|LK||Indicates a connection with the eGauge or another HomePlug AV adapter||Blinking red light when communicating with the eGauge||Blinking orange or green - possible connection with another HomePlug AV device
Off - no connection to any HomePlug AV devices
|ETH||Indicates an Ethernet line connection||Blinking green light when transmitting data||Off - may indicate an issue with network connectivity or a damaged Ethernet cable|
|HomePlug 1.0 HPE400T|
|HomePlug 1.0 HPE400T
||LED Label||Function||Typical Behavior||Other Behavior|
|Power||Adapter has power and is connected to the eGauge or another HomePlug 1.0 device||Green light when active, blinking green light when transmitting data||Off - adapter is not receiving power, or cannot communicate to the eGauge|
|Link||Indicates an Ethernet line connection||Green when active, blinking green when transmitting data||Off - issue with network connectivity or a damaged Ethernet cable|
In your breaker-panel, locate the breaker to which the eGauge is wired. This breaker should be labelled "eGauge Disconnect" or something similar. Once you locate the breaker, trip it so power is off, wait 5 seconds, then turn it back on. Normally, there is a single multi-pole breaker for eGauge, but in some cases there may be two or three separate breakers (one per phase/leg). In the latter case, turn off all eGauge breakers, leave them off for 5 seconds, then turn them all back on.
Almost all will cause issues, but will not necessarily prevent communication. A standard outlet can be installed; however this may not be allowed by code.
Some arc-fault breakers will trip when the HomePlug is connected. As of right now, eGauge Systems has no data on which models have this issue. If you come across a model that causes issues, please contact the support department
Outlet-style and strip-style both cause significant issues with HomePlug communication by filtering out the HomePlug signal. More information is available here.
The eGauge communicates with the HomePlug over the phase connected to L1. If the HomePlug is installed on the phase connected to L2, this will result in significant communication issues. For more information, refer to the phasing document available here.
In almost all cases, transformers will completely filter the HomePlug signal, resulting in a total loss of communication.
The effective range of HomePlug communications is approximately 50-100ft. Note that this distance refers to the length of wire in the walls, not a straight line between the eGauge and HomePlug. Longer wire runs will cause communication problems.
Depending on the model, the eGauge either uses the HomePlug AV or HomePlug 1.0 communication protocol. Other devices using the same protocol can cause communication issues. Note that devices using the 1.0 protocol will not interfere with devices using the AV protocol, and vice versa. Pairing the eGauge and HomePlug together can often resolve these issues. Information on pairing the eGauge and HomePlug can be found here.
The color and pattern of the LEDs on the eGauge and HomePlug can help troubleshoot communication issues. A guide to the HomePlug LED codes can be found here. A guide to the eGauge LED codes can be found here.
There are certain types of communication issues associated with older firmware versions. Keeping the eGauge firmware up to date is recommended. If you are unsure about the firmware version your device is using, refer to the instructions on checking firmware version located here.
For example: http://egaugehq.egaug.es/?lang=es Available language codes include:http://DEVNAME.egaug.es/?lang=LANGUAGE_CODE
|277V HomePlug Transformer Kit Manual||Product|
|EG30xx Owner's Manual||Product|
|eGauge2 Owner's Manual (product discontinued)||Product|
|Third-party device integration information||Product|
|CT Selection Guide||Installation|
|eGauge Configuration Guide||Installation|
|Panel Phasing and eGauge Installation||Installation|
|Cellular Modem Connectivity Diagram||Connectivity|
|eGauge BACnet PICS||Connectivity|
|eGauge XML API||Connectivity|
|Sunny SensorBox Connectivity Diagram||Connectivity|
|Tutorial 1: Configuring an eGauge for static IP||Tutorial|
|Tutorial 2: Pairing an eGauge with a HomePlug adapter||Tutorial|
|Tutorial 3: Clearing the browser cache||Tutorial|
|Tutorial 4: Using eGuard Manager||Tutorial|
|Tutorial 5: Configuring eGauge Alerts||Tutorial|
|Tutorial 6: Directly Connecting to the eGauge||Tutorial|
|Tutorial 7: Connecting via the eGauge proxy server using IE 10/11||Tutorial|
|Security Considerations||White Paper|